Allows ActiveLED® C-Type Lighting equipment in a defined Occupancy Zone to be turned off or on based upon sensed motion or occupancy, saving even more energy and therefore cost. Low DC Voltage with an effective range of 35 feet
ActiveLED® Lighting consumes at least 50-85 percent less energy than conventional lighting.
With its patented design and superior LED elements, ActiveLED Lighting is a reliable light source with a 90,000-hour lumen life, making it a maintenance-free solution for applications where changing bulbs and ballasts can be hazardous and expensive.
Significant savings from not having to maintain and renew incandescent bulbs or fluorescent tubes in light fixtures, reduced heat generation and energy use justify the initial outlay.
Additional and substantial energy savings can be achieved by implementing an environmentally safe ActiveLED lighting / occupancy zone
LightSpace® Remote Motion Sensor Application
The Remote Digital Motion / Occupancy Sensor is designed to be connected to a C-Series ActiveLED power supply. One Sensor can control one or many LED lighting fixtures, providing the ability to adjust light levels to suit occupancy needs while saving even more energy.
The digital sensor is connected to the sensor input of one ActiveLED lighting fixture using a standard 6-wire cable terminated with 6-pin RJ-12 connectors.
A group of controlled ActiveLED light fixtures (ActiveLED C-Series power supplies) can be interconnected to form an occupancy zone using a 4-wire communication link that is terminated in RJ-11 / RJ-12 connectors.
The Oblong Format ActiveLED Motion / Occupancy Sensor has an effective range of ~35 feet and a sensing cone that is 65+° from the perpendicular (135° total cone).
ActiveLED® Occupancy Zone / Lighting "Network"
Up to 999 ActiveLED lighting fixtures that can be controlled from a single ActiveLED motion / occupancy sensor. Each interconnected LED fixture / power supply relays the sensor setting to the next connected fixture, thereby giving unlimited flexibility in managing a defined ActiveLED Lighting Occupancy Zone.
Adding a digital dimmer or LightSpace Manager to the configuration offers additional management capabilites, further reducing power consumption and therefore energy costs of the lighting fixtures within the Occupancy Zone.
Depending upon the size and shape of the defined space and the number of entry and exit points, one digital dimmer and/or LightSpace Manager can be combined with up to 10 (ten) motion/occupancy sensors in designing the occupancy zone to provide the maximum energy savings.
ActiveLED® Brightness Settings and Fixture Power Consumption
ActiveLED® Brightness Settings relative to Fixture Power Consumption
The ActiveLED system architecture is unique in its efficiency, design and the way the ActiveLED Elements are driven. This chart accurately details the substantial energy savings that can be achieved when deploying a manageable ActiveLED lighting network.|
Combining this architecture with a LightSpace™ Appliance, including the LightSpace Manager-IR, provides additional energy savings that are somewhat exponential to the reduced light level.
An ActiveLED High Bay Strip with 104 watts total fixture (96 watts of LEDs) with the brightness dimmed down to brightness level 50, then the total power consumption of that fixture is 16.64 watts (16% of 104 watts) at this brightness level of 50.
An ActiveLED High Bay Strip with 104 watts total fixture (96 watts of LEDs) with the brightness dimmed down to brightness level 30, then the total power consumption of that fixture is a mere 5.2 watts (5% of 104 watts) at this brightness level of 30.
This same chart and percentages not only apply to any of our lighting fixtures with the external dimming controls, including the Rotary Digital Dimmer and the LightSpace Manager, but also to any pre-programmed ActiveLED fixture.
Although the light output of ActiveLED fixtures can be dimmed in 2% increments, the chart on the left accurately portrays the percentage power consumption for each incremental brightness setting of 10.
ActiveLED® Communication Cables for the Remote Digital Sensor
The ActiveLED® Motion Sensor connects to an ActiveLED power supply as per the EDSaP wiring specification, using either standard RJ12 6-wire "flat ribbon" or UTP cable using RJ-12 male connectors (Flat-Ribbon recommended).
Interconnect each ActiveLED lighting fixture to provide a lighting network / occupancy zone as per the EDSaP wiring specification, using either Standard RJ-11 / RJ12 (4-wire) "flat ribbon" or UTP cabling (Flat-Ribbon recommended).
NOTE: Cables not included in the price of the Motion Sensor.
Ringdale uses the latest in energy efficient LEDs and LED modules producing equivalent or greater light output than fluorescent (HID) fixtures. Our state-of-the-art electronics monitor current and temperature of the substrate to assure maximum performance under the prevailing environmental conditions and a Lumen Lifetime of 90,000 hours (90% Luminous Flux).
We provide mechanically robust LED lighting systems; our warranties are 10 years on LED elements, fixtures, drivers / power supplies and Motion / Occupancy Sensors.
Ringdale is an ISO 9001:2000 company, registered under BSI certificate FM-1880. Ringdale provides products of the highest quality designed and manufactured in Texas and in the United Kingdom.
ActiveLED® Remote Motion / Occupancy Sensor Part Numbers:
00-27-0609-0000, US format
00-27-0609-0001, UK format
|Sensor Connection to LED Light:||6-pin flat ribbon or UTP cable with RJ-12 Connectors|
|Inter-Connect, LED to LED Fixture:||4-pin flat ribbon or UTP cable with RJ-11 / RJ-12 Connector|
|Prerequisite:||ActiveLED lighting fixtures with the Digital Management option (communications ports)|
|Sensor Connection to other ActiveLED Appliances:||6-pin flat ribbon or UTP cable with RJ-12 Connectors|
|Up to 35 feet|
65° from the perpendicular (135° total cone)
Default Factory Settings:
|Powered by the attached ActiveLED fixture (12 volts DC)|
After 10 minutes of no motion, dim light down to warning level 70.
After 10 seconds of no motion, dim from L70 down to and hold at level 40.
When motion is sensed, go to full brightness.
|Regulatory Compliance:||cUL listed, CE, suitable for damp locations.
RoHS compliant. |
|3.5" x 1.3" x 1.0" (8.9 x 3.3 x 2.5 cm).|
2 ounces (0.06 Kg)
Caution! All specifications published herein are subject to change without notice. See website ActiveLED.com for Terms and Conditions of use of the website and the information provided herein. See Ringdale website on www.ringdale-technology.com for Terms and Condtions of Sale and Service.
|+44 (0)844 264 1570|