EDSaP Relay Actuator, (4) 120/240VAC Relays, EDSaP Comms Ports, 0-10 VDC, Stepper Motor Control with integrated all voltage power supply.
Connects to EDSaP motion activated sensors, daylight sensor, IR transceivers, ZigBEE radio modules and LSC Lightspace® controllers.
This device forms an integral part of the LightSpace® Building Automation System when it comes to providing energy savings without a larger building automation system or interfacing to legacy devices that are not EDSaP compliant.
The 1634 Relay Controller is the device that can turn legacy devices or non-EDSaP compliant devices ON or OFF and can generate a 0-10V control signal for the control of lighting devices, valves and other equipment that can be controlled by a 0-10V signal in 64 linear steps.
LightSpace® devices are built for maximum flexibility, performance, low-power consumption and using easy to obtain plug-in relays make for ease of maintenance.
The Relay and Stepper Motor Controller can be triggered and controlled by a multitude of LSMs and EDSaP compliant devices:
Other devices that can directly connect to the Relay Controller for applications like fan control, air conditioning control and those we have not thought of:
Motor control via programmable timers and RPM presets. Ramp-up and Ramp-down programmable via USB and application software.
EDSaP Control via LSC or Motor Control Manager (MCM)
The MCM can set RPM using the 3 button interface and 3 digit display.
Input switches can be configured to trigger motor functions.
For more information on the Ringdale LightSpace® Building Automation system www.ringdale.com/lightspace/.
Ringdale is in business for more than 30 years and deisgns and manufactures its devices within an audited ISO9000 quality system since 1986, certificate FM1880.
Part Number: 00-27-0634-0000
|Power Supply:||• 100-277V AC.• 48V DC (nominal)|
|Power Factor and THD:||PF: >0.95 (100..277V).THD: <20%, typical <10%|
|Power Consumption:||Max: 56 Watts|
Standby: 1 Watt no external devices connected
|EDSaP Communication:||COM-1 and COM-2 ports, unit repeats|
|Programming Port:||USB-2 port requires PC or Laptop and application software|
|Motor Control:||Requires Ringdale Stepper Motor Driver Boards|
max 20 Watts per channel
|Relay Outputs:||4 x Socket Relays: Single Pole - Normally Open|
5A / 250V (derate for DC operation)
Relay outputs are potential free
DO NOT OPERATE ABOVE 300V AC
|Switch Inputs:||Digital TTL logic signals or just connect potential free switch (see instructions)|
Caution! All specifications published herein are subject to change without notice. See website ActiveLED.com for Terms and Conditions of use of the website and the information provided herein. See Ringdale website on www.ringdale-technology.com for Terms and Condtions of Sale and Service.
|+44 (0)844 264 1570|